Find great deals for Gamewell Flex If LCD Display With CPU Fire Alarm Board ASSY If Shop with confidence on eBay!. The Gamewell Retrofit Kits offered by Gamewell-FCI provide a simple way to convert without replacing the existing Gamewell backbox. IF panel. Gamewell IdentiFlex Fire Alarm Control Panel. FIRE ALARM AND SMOKE DETECTION SYSTEM. 1. GENERAL. RELATED DOCUMENTS.
|Published (Last):||18 May 2006|
|PDF File Size:||5.66 Mb|
|ePub File Size:||12.83 Mb|
|Price:||Free* [*Free Regsitration Required]|
• View topic – Gamewell IF heat detector false alarms
Previous topic Next topic. Wed Sep 24, 6: It is true that the, and panels are not made any more. The fire alarm company who was “maintaining” the system for the last 5 years of if160 does not know anything about this?
The location is inside the elevator machine room on the roof top of a 10 story tower in Long Beach. Either way I would look into the E3 as a solution for the Gamewell I am in charge of a large school building and am being told that my fire alarm panel is obsolete and that parts are not available.
Recently, UL updated it’s fire alarm standards from 8th edition to 9th edition.
Gamewell If610 Gw31026 Y Fire Alarm Front Control Panel Display
Did you miss your activation email? This way the customer has a system that is new and up to code as well as being able to purchase the apollo devices when needed. There are replacement parts available though. The GW will gzmewell show a trouble or anything system normal.
Heat detectors associated with elevator control should always be fixed temperature only, not ROR, in order to activate prior to the sprinkler head.
The Truth gamwell Thermodynamics: Mon Sep 22, 5: This works great too. If you have any Q’s let me know. Hello everyone, I’ve exhausted all of my outside resources now troubleshooting the cause of if601 alarms from a XPT addressable heat detector on an IF system. We have literally hundreds of customers that have older gamewell systems in them.
The cost on parts for the is NOT going to go down but rather UP as parts become less and less available.
That being said, what temperature rating sprinklers are installed? With care and maintanence, commercial grade smokes last a long time, but a facility like a school is a pretty iv610 use environment. Please login or register. Now a few years later the system gets swapped out with an E3 system and all of a sudden there is an extra address trouble on the panel.
IF that is the case, then would anyone happen to have the software that I need to change the device address and the related functions in the program?? Not familiar with that model, but chances are, he’s right.
The GW is a good panel. Most of the colleges that have a lot of Gamewell systems have a decent ammount of spare devices in stock in their maintenance area.
I’ve replaced the detector and now the base, but the issues continue. You cannot post new topics in this gamedell You cannot reply to topics in this forum You cannot edit your posts in this forum You cannot delete your posts in this forum You cannot post attachments in this forum.
January 16, You do not have the required permissions to view the files gamewelll to this post. The company I work for has been with Gamewell for over 40 years.
IF Datasheet(PDF) – Gamewell-FCI by Honeywell
I don’t know if they’re still in business as the company making the city master fire alarm boxes but the fire alarm panel line became Gamewell-FCi and then got swallowed up into the Honeywell cluster.
They merged under the Honeywell umbrella. January 15, ,